In the Brinnon area, Eagle Pipe Heating & Air is well known for providing exceptional furnace repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with Eagle Pipe Heating & Air because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC, Gas Pipe, & Furnace Repair in Brinnon, WA. Call us today at (206) 765-6851!
Install done by Alan, Colton, and Dylan
Defrost Control Board, OEM Part # PCBDM133S Done by Colton
Pulled out 8 pounds and 5 ounces of refrigerant out of the system (overcharged). System should only have seven pounds from the factory and 4 ounces added in for line set. System was getting restricted at the piston and the filter dryer. Piston was removed and was bunked up in and around itself. The filter dryer had a six degree split over it which is only supposed to have at max a four degree split. New filter dryer was put in and piston was removed for now. System also needs new king valve assembly because the king valve was not going up or down and that could also be a restriction. System was left on emergency heat for now unit we get a new king valve assembly with a new piston for the unit. Piston size is labeled on the heat pump name plate
Precision Tune Up
Service call to replace break on panel
Furnace service call & repair
Service & repairs on heat pump system
Service call to diagnose and fix furnace issue.
Installation of ductless mini split.